Specification for Liquid Immersed Power Transformers 500 kVA â€“ 10,000 kVA Up To 34.5 kV HV Winding
This document defines the requirements for design, manufacture and testing of oil filled transformers intended for use on the PCO OIL Projects in Iraq.
2. CODES AND STANDARDS
The electrical equipment and installation shall conform in design, materials and performance, except where otherwise specified, with the current issue
and amendments of the Codes and Standards specified by the International Electrotechnical Commission (IEC).
All conflicts between the requirements of this specification and other relevant documents shall be referred to the Buyer for resolution.
2.2 International Electro-technical Commission
IEC 60044 Instrument Transformers
IEC 60071 Co-ordination of insulation.
IEC 60076 Power transformers.
IEC 60137 Bushings for alternating voltages above 1000 V.
IEC 60214 On-load tap-changers.
IEC 60296 Specification for unused mineral insulating oils for
transformers and switchgear.
IEC 60354 Loading guide for oil-immersed power transformers.
Identification of equipment terminals and of terminations of
certain designated conductors, including general rules for
an alphanumeric system.
IEC 60529 Degrees of protection provided by enclosures.
IEC 60542 Application guide for on-load tap-changers.
IEC 60551 Determination of transformer and reactor sound levels.
IEC 60616 Terminal and tapping markings for power transformers.
IEC 60722 Guide to the lightning impulse and switching impulse testing
of power transformers and reactors.
IEC 60947 Low voltage switchgear and control gear.